The apparatus shall be equipped with a Harrison Hydra-Gen hPower Idle Control System (ICS).
The ICS shall be provided in a single environmentally protected enclosure that will house all the required components; external mounting of components is not accepted.
The following components shall be required with the ICS:
Lithium-Ion Batteries; Lead-acid batteries are not accepted.
Battery Control Module to monitor and report the battery health.
System Control Module shall be designed to communicate via CAN data bus or via hardwire.
DC/AC Inverter (optional) with a 20-amp twist-lok mounted in the unit
The ICS shall have 90 minutes at 150 amps (225-amp hours) with 2-batteries or 120 minutes at 150 amps (300-amp hours).
The ICS shall Std Charge via Apparatus alternator (12 VDC charge version)
The ICS shall Rapid Charge via Harrison generator (120 VAC charge version)
The ICS shall include 2 Lithium-Ion Batteries std with a 3rd battery as optional.
The ICS shall include 1 battery charger for the 12 VDC Standard Charge system.
The ICS shall include 2 battery chargers for the 120 VAC Rapid Charge systems, with an option for a 3rd battery and battery charger.
The ICS shall provide removable service access panels to all serviceable components.
The ICS environmentally protected enclosure shall have a 3” riser to protect it from water intrusion.
The ICS shall have the capability to monitor and display the AC frequency, AC voltage and AC amperage of the inverter per NFPA 1901.
When properly installed, the ICS shall be warranted for a period of not less than two (2) years or 2000 hours, whichever should come first.